The 6000 Series, the newest addition to the PowerMatic® Family of Operators combines intelligence, reliability and superior control in one package. Designed with the user in mind, this operator features simple to use electronics, an onboard power supply and easy integration into access control systems.
Designed for moderate to high traffic applications, this operator has a two-piece sub-assembly for easy installation and LCD screen for clear and accurate read-out of operating settings. Available for push or pull side mounting, the 6000 Series can be operated manually or activated via wall switches or radio frequency devices. This reliable unit ensures consistent opening and closing based on dual mode, electrohydraulic technology and is ideal for hospitals, office buildings, sports arenas or government facilities.
Door Controls (interior)(exterior) swinging door(s) shall be of rack and pinion design contained within a precision cast aluminum housing. Door closing force shall be adjustable to ensure adequate closing control. Door closing speed shall be controlled by independent hydraulic adjustment valves in the sweep and latch range of the closing cycle. Door Operator shall provide conventional door closer opening and closing forces unless the power operator motor is activated. Door Operator opening force and speed shall be adjustable in the inverter/interface module's LCD screen to ensure adequate opening control per accessibility codes. Door Operator shall have an adjustable hydraulic backcheck valve to cushion the door speed if opened violently. Door Operator shall utilize the inverter/interface module's LCD screen and joystick to establish door closes and open positions. [(Door Operator shall be AUTOMATICALLY ACTIVATED by either a slight push or pull in the direction of opening swing – Push and Go.) (Door Operator shall be SELECTIVELY ACTIVATED by external initiating device, i.e. wall switch, etc.) (Door Operator shall be both AUTOMATICALLY ACTIVATED and SELECTIVELY ACTIVATED.)] Unit shall include "E-saver" feature to automatically recognize abled body traffic and immediately trigger door to close after sensing no forces on door. Unit shall have delay for motor activation, electric lock interfacing, and hold open time. Units shall have SPDT relay for interfacing latch retraction exit devices or similar products and have 24VDC @ 1.3A output for connection of electric strike, lock, radio frequency receiver, etc. Units shall have Vestibule sequencing input for operation of two or more units. Unit shall have smoke ventilation inputs to power open doors when activated by fire or smoke alarm. Unit shall have a three-position Selector Mode Switch that will permit the unit to be switched “ON”to monitor for function inputs, switched to “H/O” for indefinite hold open function or switched “OFF” which will disable function inputs allowing unit to be used as a manual door closer. Unit shall be ETL tested to UL standards for automatic closing door. The Unit shall be adjustable to provide compliance with the requirements of the Americans With Disabilities Act (ADA). Unit shall be certified by BHMA to meet ANSI A117.1 and A156.19 requirements. Unitshall meet UL, cUL, UL10C and UL10B standards.
Additional Specifications for FunctionsFor Power Operator Function:When activated, the unit shall, by means of a motor, chain and closer, power open the door at both a speed and force that are adjustable to accessibility codes. The door shall be powered from a door closed position to a full door open position and remain in momentary hold open for 5 seconds minimum (adjustable 0 to 30 seconds in 1 second increments). [(Unit shall power open door to full open position up to 110°.) (Unit shall be capable of openingdoor manually from 110° – 180°.)] Once unit reaches full hold open position, if reinitiated, unit’s momentary hold open time shall restart from the maximum set time. If unit is initiated during the closing cycle, unit shall revert to opening cycle beginning at that door position. Unit shall have a toggled hold open input that upon first initiation will power door to a maintained hold open position; a second initiation will allow door to close. Unit shall have obstruction detection on closing, which will reverse the closing door to the full open position then re-attempt to close door after momentary hold open time has elapsed. Obstruction detection on opening shall shut motor off, allowing door to close under spring force. These obstruction detection features shall be integral to unit. During closing cycle, the unit shall close door under full spring power not to exceed a closing force of 15 lbf
Published 21 Mar 2013
Customer Service:800.438.1951 x Ext 6701(8am - 4:30pm Eastern)
Technical Product Support:800.438.1951 x Ext 4706(8am - 4:30pm Eastern)
Sales Agency Locator
- Examination rooms
- Main entrance doors
Colleges or Universities
- Entrance doors
- Common areas
- Dormitory entrances
ETL tested to UL/ULc standards for automatic doors used on fire and smoke barrier doors and CSA C22.2 No. 247 for operators and systems of doors
ANSI/BHMA A156.19 certified
Americans with Disabilities (ADA)
Meets requirements for UL10C for positive pressure
2-year limited warranty
ASSA ABLOY, the global leader in door opening solutions
© Yale Security, Inc., an ASSA ABLOY Group Co. 2015| Legal | Cookies | Email: